Markel J3485A1 Recess Mounted Ceiling Heater, 5KW, 208V 3PH 13.9A
Usually Ships In 4 Weeks
Free ground shipping to the lower 48 states
- Product ID:
- 50.00 (Lbs.)
- Ships By:
- Free Ground
- Ships From:
- Tennessee - Factory Direct
Frequently Bought Together
Total Price:Add to Cart
Please choose options for all selected products
- White powder coated 20 gauge grill.
- All units have manual reset thermal limit, 24V control transformer, and 24V relay (A1 suffix).
- Enclosed steel fin sheath element.
- Rough in dimensions: 23-1/16” sq. x 9-1/8” deep.
- Made in U.S.A.
Contractor shall supply and install heavy duty ceiling mounted forced air electric heater(s) of the wattage, voltage and phase as indicated on the plans. The heater shall be so designed to provide an even distribution of heated air to the space to be heated by drawing return air in the periphery of the heater, across and through the element and be discharged from the center section of the heater by means of an electric motor and axial flow fan blade.
Heaters shall be recessed type and mounted flush with the finished ceiling. The return grille assembly shall be constructed of a one piece heavy gauge steel with 1/4” slots for return air and concentric rings for uniform air discharge. Grille assembly shall be attached to chassis by tamper-resistant (allen head) machine screws. All parts of enclosure shall be heavy gauge steel, zinc coated both sides and finished in neutral off white powder coat paint.
Enclosure shall be constructed of 1/6” x 3/8” rounded edge horizontal steel louvers which shall be spaced for maximum opening of 5/16”. Louvers shall be welded at every intersection to evenly spaced 1/8” diameter vertical members. Discharge grille to have concentric rings for uniform air discharge. Grille assembly shall be attached to chassis by tamper-resistant (allen head) machine screws. All part of enclosure shall be heavy gauge steel, Zinc coated both sides and finished in neutral off white colored powder coat finish.
Motor shall be permanent lubricated, unit bearing, totally enclosed, impedance protection. Motors shall operate at no more than 1300 RPM and shall be same voltage as the heater.
Heaters shall have a rating of 600 CFM at 1,000 F.P.M. with a maximum temperature rise of 44 degrees F.
Element assemblies shall consist of two or three corrosion resistant steel sheathed type elements mechanically bonded to common corrosion resistant steel fins. Each sheathed element shall consist of helically coiled Nickel Chromium alloy resistant wire completely embedded in and surrounded by magnesium oxide, enclosed and wedged into corrosion resistant steel sheaths. Elements shall have 2 inch cold conductor pins extending into sheath and shall have a density of no more than 60 Watts per inch.
Heaters shall be equipped with a manual reset thermal overload which disconnects elements and motor in the event normal operating temperatures are exceeded. For safety, if opened due to abnormal temperature, thermal overload shall remain open until manually reset. Automatic reset thermal overloads which allow the element to continue to cycle under abnormal conditions will not be accepted. Heaters shall be ETL listed.
Recently viewed products
Markel RCP123 22.50 Inch x 22.50 Inch Recess Mounted Radiant Ceiling Panel, 0.375KW, 120/240V 1PH 3.1/1.6A