Markel HF2HUH10C03 Horizontal Heater, 10/7.5KW, 240/208V 1/3PH 41.7/24.1/36.1/20.8A
Usually Ships In 10-15 Business Days
Free ground shipping to the lower 48 states
- Product ID:
- 45.00 (Lbs.)
- Ships By:
- Free Ground
- Ships From:
- Tennessee - Factory Direct
Frequently Bought Together
Total Price:Add to Cart
Please choose options for all selected products
Heavy Gauge welded steel cabinet with powder coated finish and control compartment with a hinged and latched access door, simplifying wiring installation & maintenance.
Circular copper clad steel sheath element with continuously brazed steel fins formed to match the air delivery pattern of the fan blade.
All units come equipped with automatic resetting type limit controls to deenergize the heater should an over-temperature situation occur.
FAN and MOTOR:
Totally enclosed, single phase, permanently lubricated, thermally protected motors with unit bearings on 3 KW - 10 KW models and sleeve bearings on 12.5 KW - 48 KW models - mounted with rubber insulators to minimize vibration and noise. Fan assembly enclosed by a heavy Gauge, close spaced, chrome plated wire guard.
Louvers are individually adjustable for directional control of air flow and the entire assembly can be repositioned in the field from down flow to up flow or left / right directional air flow.
20 KW through 48 KW units and all 480V have built in 24 Volt transformer for low voltage remote thermostat application. 25 KW through 48 KW models available in 2-stage on special order (consult factory).
Unit Heaters can be mounted with the motor shaft from horizontal to downward at 45° off horizontal. Pre-drilled holes and installed threaded nuts provided to allow hanging by threaded rods - 1/4” for units up to 15 KW and 5/16” for 20 KW units and larger. Optional wall / ceiling mounting brackets are available for all units.
NOTE: Louver assembly is square and mounted with screws. Louver can be removed and repositioned for four (4) directional air flow - left - right - up - down with the heater in the horizontal position.